|Requestor||COCHRAN, RONALD E|
|Alt Requestor||DANGELSER, BRIAN|
|Description||LLOYD CORRECT AIR HANDLER PROBLEMS IN BUILDING|
|Details||No estimate requested, project will be approved
ITEMS: HEATING/COOLING SYSTEM
AHU's were never able to stay on line in cold weather since building built. Maintenance staff had to unhook face and by pass dampers to keep units running. Per Brian Dangelser Johnson programmed them to be for conventional face and bypass not intergal and even if programed right will not work because project did not install termostatic vents on steam coils and once this is corrected valves need to be evaluated for proper sizing.Issue to correct problems.
Location: LLOYD VETERINARY MEDICAL CENTER AHU 12, 13, 14, 15,16,17,18
Desired completion date: NOVEMBER 2011
Known time constraints: Warranty?
Desired project cost: UNDER $1000
Funding Contact: VAN WYK, LOLA G
|Status||PROJECT COMPLETED AND CLOSED OUT
|Close Date||12/13/2012 3:39:38 PM|
Questions about this request should be directed to the FP&M Project Coordination Center.